Case Study - Fridges are fallible. How a defrost went wrong
It all started when…
A recent installation of MimoCool is successfully monitoring medication and food fridges in the supported care facility.
Sensors were placed in the kitchen freezers which immediately began reporting back to the MimoCool gateway on the floor above.
Before activating alerts and final handover, final checks were carried out by MimoCool and user staff. To their surprise they discovered a freezer had been off line for a while before coming back on stream again. Discussions with staff indicated that they were unaware this had happened and felt this could only occur if the power was switched off.
However further analysis of the plotted temperature showed that the freezer had started its regular 6 hourly defrost but had failed to restart its freezing cycle. Result was a steady climb of temperature before the freezer re-engaged hours later.
Richard Jenkins of QVisual.co.nz commented. “This just emphasises the need to continuously monitor as things can happen quickly and need to be contained. Thats what MimoCool does well. Needless to say the alerts are now activated and live so any re-occurrence can be picked up within 30 mins of starting.”